The single room temperature controller FloorControl is a complete system consisting of a terminal block with the corresponding number of room thermostats. The controller terminal bar has eight control circuits. One room thermostat is required per control circuit; it is wired to the controller terminal bar. Up to four thermostatic actuators can be connected to each of the control circuits 1 to 3; a maximum of two actuators can be connected to the thermostatic actuators 4 to 8. The room thermostat measures the actual temperature in the corresponding rooms. The reference temperature is adjusted by means of the keys of the room thermostat. The room thermostat then switches the thermostatic actuator via the controller terminal bar to control the heating circuit at the manifold.
WB 01 D-8-24: Power supply for the thermostatic actuators (DC 24 V) and supply of the contacts of the room thermostat (battery operation only)
WB 01 D-8-230: Power supply for the thermostatic actuators (AC 230 V) and supply of the contacts of the room thermostat (AC 230 V or battery operation only)